Dry leg means in lab.. And wet leg means in feild
A positioner is a device put into a valve to ensure that it is at a correct position of opening as per the control signal. An I/P converter only sends the opening/closing request to valve but can not confirm its position.
Positioner senses the valve opening through a position feedback link connected to valve stem which is its input signal. I/P converter output is its setpoint input. The difference between these two is the error signal based on which the positioner positions the valve to correct position to reduce error to zero. Hence positioner is nothing but a pneumatic feedback controller. Controlled external supply air to positioner provides power to positioner to position a valve. Also positioner is used in a valve when valve operating signal range is different from I/P converter output range.
An electric potential is developed when a conductor is moved across the magnetic field. In most electrical machinery the conductor is a wire. The principle is equally applicable to a moving, electrically conductive liquid. The primary device of commercial magnetic meters consist of straight cylindrical electrically insulated tube with a pair of electrodes nearly flush with the tube walls and located at opposite end of a tube diameter. This device is limited to electrically conducting liquids. The magnetic meter is particularly suited to measurement of slurries and dirty fluids.
Turbine meters consist of straight flow tube within which a turbine or fan is free to rotate about it s axis which is fixed along g the centre line of the tube. Mostly, a magnetic pick up system senses the rotation of the rotor through the tube walls. The turbine meter is a flow rate device
, since the rotor speed is directly proportional to the flow rate. The output is usually in the form of electric pulses from the magnetic pick up with a frequency proportional to the flow rate.
The most common range for differential range for liquid measurement is 0-100. This range is high enough to minimize the errors caused by unequal heads in the seal chambers. It is also dependent on the differences in the temperature of the load lines. The 100 range permits an increased in capacity up to 400. While decrease down up to 20 by merely changing the range tubes or range adjustments.
Variable area meters are special form of head meters. Where in the area of flow restrictor is varied. So as to hold the differential pressure constant. The rota meter consists of a vertical tapered tube through which the metered fluid flows in upward direction. As the flow varies the ‘float' rises or falls to vary the area of the passages that the differential across it balances the gravitational force on the ‘float'. The differential pressure is maintained constant. The position of the ‘float' is the measure of the rate of flow.
When, in some processes, e.g. batch processes, long transient responses are expected during which a sustained deviation is present the controller integral action continuously drives the output to a minimum or maximum value. This phenomenon is called ‘integral saturation of the control unit'. When this condition is met, then this unit is de-saturated.
In automatic reference junction compensation, variable nickel resistor is used. As the temperature changes, so does its resistance. This reference junction compensator is located, so that it will be at the temperature of the reference junction. The reference junction is at the poset where the dissimilar wire of the thermocouple is rejoined. This joint is invariably at the terminal strip of the instrument.
A solenoid is electrically operated valve. It consists of solenoid coil in which magnetic plunger moves. This plunger is connected to the plug and tends to open or close the valve. There are two types of solenoid valves:
1. Normally Open
2. Normally closed
Use: It is used for safety purpose in different electric work
A ratio control system is characterized by the fact that variations in the secondary variable don't reflect back on the primary variable. A ratio control system is the system where secondary flow is hold in some proportion to a primary uncontrollable flow.
If we assume that the output of a primary transmitter is A. and the output of the secondary transmitter is B, and that the multiplication factor of the ratio relay is K, then for equilibrium conditions which means set valve is equal to measured valve, we find the following relation:
KA-B=0 or B/A = K where ‘K' is the ratio setting off the relay.